550 High Street, Suite 220, Auburn, CA 95603; (530) 823-0706, Fax 530-823-6937,
Fire Protection Contractor magazine A Magazine Built on Education and Open Communication for Over 35 Years
The Most Widely-Read Fire Sprinkler Industry Publication
Fire Protection Contractor magazine
550 High Street, Suite 220, Auburn, CA 95603
(530) 823-0706 Fax 530-823-6937
FPC Now Accepts Credit Cards!
For new subscriptions and renewals, click the "Subscribe" button.
To pay an invoice, please e-mail a request to email@example.com
FPC magazine is not available online, and all subscriptions are paid.
Please visit the "What's New" page for News, Calendar items, and industry developments.
* Counterfeit Sprinkler Warning *
UL Warns of Counterfeit Fire Sprinklers (Release 14PN-9)
The following is a notification from UL that the fire sprinklers identified bear counterfeit UL Certification Marks for the United States and Canada. The fire sprinklers have not been evaluated by UL to the appropriate Standards for Safety and it is unknown if the fire sprinklers comply with any safety requirements.
Although the fire sprinklers wrench boss is marked "TYCO" and the thermo bulbs are marked "JOB F5" the fire sprinklers were not manufactured or labeled by Tyco and the thermo bulbs were not manufactured or labeled by Job, GmbH., affiliates or agents.
Name of Product: Upright TY3151; Pendent TY3251; Horizontal Sidewall PS007.
Location: The sprinklers have been found in Vietnam and India. UL has not received reports of these counterfeit sprinklers in other locations.
Identification: On the product: The product bears counterfeit UL and TYCO Marks and the following information on the upright TY3151 sprinkler. (Location - Vietnam)
Counterfeit Fire Sprinkler Markings include: UL in a circle, 155°F/68°C, TY3151; "TYCO" cast into both sides of the wrench boss; Deflector material zinc plated steel (magnetic); 5mm glass bulb -Job F5.
Authentic Fire Sprinkler Markings include: cULus in a circle, 155°F/68°C, SU, TY3151; "TYCO" incised on one side and the year of manufacture on the opposite side of wrench boss; Defector material brass with chrome or painted white (non-magnetic); 5 mm Geissler glass bulb - "G" between two triangles on one side and lot number on the other side.
For more information and to see photographs go to www.ul.com.
See our Classified section for all classified ads including new, unpublished ones.
Contact the Webmaster to make suggestions and comments.
Please be Sure to see FPC's Editorial page to see how you can be included in FPC! Or, send your news to:firstname.lastname@example.org
Send us an e-mail if you want to be added to our "contacts" list so we can send you important industry information.